For an overcurrent relay coordinated in a power system network, it was observed that relay, the following tripping times were observed:
1- For phase-ground fault, double phase-to-ground fault and three phase to ground fault result in tripping time of 0.5141s
2- For phase to phase fault, the tripping time is 0.5389s
Why does it take more time for that relay to operate for phase-to-phase fault? Please clarify.
I have drawn characteristic of overcurrent relay. The y-axis has operating time and the x-axis has per unit fault current. As we can see as the fault current increases operating time decreases.
I have made simple calculations taking the reactances of practical power system and foundd LG fault current and LL fault current for the same system. we can see that the fault current for an LG fault is greater than that for an LL fault. Here the fault considered our dead shot circuits i.e. no fault impedance has been included while analysing the fault currents. Thus for higher currents the operating time is lesser it means that the operating time for LG fault will be lesser than LL fault.
One more factor for a constructional feature of an overcurrent relay also suggest us the reason for this if we look at the construction of an overcurrent relay. We can see a rotating disc placed between poles of an electromagnet that is energized by a coil carrying a part of current (fault current). As the magnitude of current increases the speed of rotation of the disc also increases. Greater the current, greater is the force and hence more speed. This brings the movable contact in contact with trip contact faster than that when the current is lower. As soon as the trip contact closes, the relay trips. Thus for higher currents the disc will move faster and will trip the relay faster hence taking list tripping time.
Hope I have answered your question.
Please rate a thumbs up if satisfied.
Have a nice time ahead:)
For an overcurrent relay coordinated in a power system network, it was observed that relay, the...
Step by step precise and concise full solution please A distribution board distributes energy to various items of plant via an installation which has a high voltage (H.V.) panel, a low voltage (L.V) panel and a transformer. The details are as follows: The H.V. panel obtains a 3-phase supply at 11 kV. The transformer circuit-breaker is equipped with 75/5A current transformers which feed a very inverse 3-poles overcurrent relay of 5-A rating. The transformer has a rating of 1000 kVA...
can you calculating this question and explain why? thanks A distribution network shown in Figure 3 consists of a 40-MVA and 33/22-kV step-down transformer with a reactance of 10% and two distribution lines each having a reactance of 5 Q2. The load connected to each bus is also shown in the figure. The CO-8 overcurrent relays are used to protect the system. The time-current curve of the CO-8 relay is shown in Figure 4 on page 5. Assume that the...
Part B (20 marks) Figure 2 shows a three phase 22kV, 50Hz radial system, which is to be protected by two inverse- time over-current relays B1 and B2. The maximum loads for this system are L 6 MVA, and L2- 5 MVA. The maximum fault currents at bus 1 and bus 2 are 1500A and 1000A respectively. The minimum fault currents at bus 1 and bus 2 are 900A and 650A respectively The line currents are measured using current transformers...
The single-line diagram of a three-phase power system is shown. Equipment ratings are given as follows: The inductor connected to generator 3 neutral has a reactance of \(0.05\) pu using generator 3 ratings as a base.1. Draw the zero-, positive-, and negative -sequence reactance diagrams using a \(1000 \mathrm{MVA}, 765 \mathrm{kV}\) base in the zone of line \(1-2\).2. Faults at bus 2 are of interest. Determine the Thevenin equivalent of each sequence network as viewed from the fault bus. Prefault voltage...
The zero-, positive-, and negative-sequence bus impedance matrices for a three bus power system are given below 5. T0.10 0.15 0.121 Bu0.15 0.10 0.08 pu [0.16 0.10 0.15] Lo.15 0.14 0.30 0.12 0.08 0.35 ZBus ZBus0.10 0.20 0.14 pu Determine the per unit fault current and the bus voltages during fault for (a) A bolted three-phase fault at bus 2. (b) A bolted single line-to-ground fault at bus 2. (c) A bolted line-to-line fault at bus 2 (d) A bolted...
The reactance data for the power system shown in figure 10.30 in per unit on a common base is as follows: *************Remember calculations are needed at bus 2 **************** 10.15. The reactance data for the power system shown in Figure 10.30 in per unit on a common base is as follows Item X1 G1 0.10 0.10 0.05 G2 0.10 0.10 0.05 T, 0.25 0.25 0.25 T 0.25 0.25 0.25 Line 1-2 0.30 0.30 0.50 Ti 1 3 2 FIGURE 10.30...
Exercise 3 Consider a 2 generator 4 bus power system shown in Figure E3. The impedance data of the network in p.u. are given in Figure E3. A bolted symmetrical three phase fault occurs at bus 4. Assuming the prefault bus voltages as I p.u., calculate the fault current and the current delivered by the generators during the fault and the bus voltages during the fault. j0.12 0.05 0.16 j0.18 j0.12 0.15 0.05 j0.12 j0.1 j0.14 4 (2 Figure E3:...
A simple three-phase power system is shown in Figure 2. Assume that the ratings of the various devices in this system are as follows: • Generators G1, G2: 40 MVA, 13.2 kV, = 0.15 pu, = 0.15 pu, = 0.08 • Generator G3: 60 MVA, 13.8 kV, = 0.20 pu, 0.20 pu, - 0.08 • Transformers T1, T2, T3, T4: 40 MVA, 13.8/138 kV, X1 = X2 = 0.10 pu, XO 0.08 pu Transformers T5, T6: 30 MVA, 13.8/138 kV, X1 = X2...
The one-line diagram of a simple power system is shown in Figure 1. The neutral of each generator is grounded through a current-limiting reactor of 0.25/3 per unit on a 100-MVA base. The system data expressed in per unit on a common 100-MVA base is tabulated below. The generators are running on no-load at their rated voltage and rated frequency with their emfs in phase. Determine the fault current for the following faults giving Zo = 0.35, Z = 0.22...
Assume a round-rotor generator delivering power in the steady state to a load bus through two transformers and a transmission line. The topology of the system is shown as below XL Хо Xi/2 XP Figure Q5 Parameters are as follows: G: Xgi -0.10 TI: Х,1-0, 10 12: XT2-0.20 0.40 Initial state: E1-1 .6 ,見= 1.6 (a) Please determine the maximal real power that can be delivered through the transmission system. (b) Please determine 6 at the steady state. (c) Assume...